Pulse aquí para ver en español
Lead Testing Results for Groner K-8
To the students, staff and parents of Groner K-8,
Over the summer, we conducted water testing at all District facilities and have been awaiting the results, which are coming in one-by-one. We just received results from Groner K-8, where 46 possible sources of drinking water were tested. Testing included the collection of two water samples at each source. Testing of the first samples indicated an elevated level of lead at 4 of the water sources (see locations below). However, testing of the second samples at these locations indicated that all were below the EPA’s action level of 20 parts per billion (ppb). That means the source of the lead was in the fixture itself. Therefore, the fixtures at all four of these locations will be replaced this afternoon and the water sources will remain in service.
Please visit the Environmental Testing page on the District website for additional information.
Water sources with initial results showing an elevated lead level:
- E Corridor, Library Sink Faucet – CLEAR
- E Corridor, Room 6 Sink Faucet – CLEAR
- E Corridor, Room 9 Sink Faucet – CLEAR